#-MIBFILE: cpqcmc.mib

CPQCMC-MIB DEFINITIONS ::= BEGIN


compaq OBJECT IDENTIFIER ::= { enterprises 232 }
DisplayString ::=
	OCTET STRING

PhysAddress ::=
	OCTET STRING

mib-2 OBJECT IDENTIFIER ::= { mgmt 1 }
system OBJECT IDENTIFIER ::= { mib-2 1 }
sysName OBJECT IDENTIFIER ::= { system 5 }
mib-2 OBJECT IDENTIFIER ::= { mgmt 1 }
sysContact OBJECT IDENTIFIER ::= { system 4 }
sysLocation OBJECT IDENTIFIER ::= { system 6 }
sysDescr OBJECT IDENTIFIER ::= { system 1 }
cpqCmc OBJECT IDENTIFIER ::= { compaq 153 }

cpqCmcMibRev OBJECT IDENTIFIER ::= { cpqCmc 1 }

cpqCmcComponent OBJECT IDENTIFIER ::= { cpqCmc 2 }

cpqCmcInterface OBJECT IDENTIFIER ::= { cpqCmcComponent 1 }

cpqCmcOsCommon OBJECT IDENTIFIER ::= { cpqCmcInterface 1 }

cpqCmcDevice OBJECT IDENTIFIER ::= { cpqCmcComponent 2 }

cpqCmcSetup OBJECT IDENTIFIER ::= { cpqCmcDevice 2 }

cpqCmcSetupConfig OBJECT IDENTIFIER ::= { cpqCmcSetup 1 }

cpqCmcSetupGeneral OBJECT IDENTIFIER ::= { cpqCmcSetupConfig 1 }

cpqCmcSetupEvents OBJECT IDENTIFIER ::= { cpqCmcSetupConfig 2 }

cpqCmcSetupTemp1 OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 1 }

cpqCmcSetupTemp2 OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 2 }

cpqCmcSetupFan1 OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 3 }

cpqCmcSetupFan2 OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 4 }

cpqCmcSetupVoltage OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 5 }

cpqCmcSetupHumidity OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 6 }

cpqCmcSetupInput1 OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 7 }

cpqCmcSetupInput2 OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 8 }

cpqCmcSetupInput3 OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 9 }

cpqCmcSetupInput4 OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 10 }

cpqCmcSetupLock1 OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 11 }

cpqCmcSetupLock2 OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 12 }

cpqCmcSetupSmoke OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 13 }

cpqCmcSetupShock OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 14 }

cpqCmcSetupAux1 OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 15 }

cpqCmcSetupAux2 OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 16 }

cpqCmcSetupAlarm1 OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 17 }

cpqCmcSetupAlarm2 OBJECT IDENTIFIER ::= { cpqCmcSetupEvents 18 }

cpqCmcSetupClock OBJECT IDENTIFIER ::= { cpqCmcSetupConfig 3 }

cpqCmcSetupThreshold OBJECT IDENTIFIER ::= { cpqCmcSetup 2 }

cpqCmcTraps OBJECT IDENTIFIER ::= { cpqCmcSetup 3 }

cpqCmcValues OBJECT IDENTIFIER ::= { cpqCmcDevice 3 }

cpqCmcStatus OBJECT IDENTIFIER ::= { cpqCmcDevice 4 }

cpqCmcControl OBJECT IDENTIFIER ::= { cpqCmcDevice 5 }

cpqCmcLog OBJECT IDENTIFIER ::= { cpqCmcDevice 6 }

cpqCmcMibRevMajor OBJECT-TYPE
	SYNTAX INTEGER (1..65535)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The Major Revision level.
A change in the major revision level represents a major change
in the architecture of the MIB. A change in the major revision
level may indicate a significant change in the information,
correct interpretation of data may require a MIB document
with the same major revision level."
	::= { cpqCmcMibRev 1 }


cpqCmcMibRevMinor OBJECT-TYPE
	SYNTAX INTEGER (0..65535)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The Minor Revision level.
A change in the minor revision level may represent some minor
additional support, no changes to any pre-existing information
has occurred."
	::= { cpqCmcMibRev 2 }


cpqCmcMibCondition OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	ok(2),
	degraded(3),
	failed(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The overall condition (status) of the system (rack(s)) represented by
this MIB.
(2) OK
(3) a minor problem, warning condition (yellow LED on CMC)
(4) a major problem (red LED on CMC)"
	::= { cpqCmcMibRev 3 }


cpqCmcOsCommonPollFreq OBJECT-TYPE
	SYNTAX INTEGER (0..65535)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The Insight Agent's polling frequency.
The frequency, in seconds, at which the Insight Agent requests
information from the device driver.  A frequency of zero (0)
indicates that the Insight Agent retrieves the information upon
request of a management station, it does not poll the device
driver at a specific interval."
	::= { cpqCmcOsCommon 1 }


cpqCmcDeviceCondition OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	ok(2),
	overloadDC(3),
	fuseDC(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Condition of CMC device,
(3) an overload of the 24V DC supply to the connected accessories occurred
(4) the overload-protection (fuse) has released "
	::= { cpqCmcDevice 1 }


cpqCmcsetLanguage OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	english(2),
	french(3),
	italian(4),
	german(5),
	spanish(6),
	dutch(7),
	japanese(8)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Language of LCD"
	::= { cpqCmcSetupGeneral 1 }


cpqCmcsetTempUnit OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	celsius(2),
	fahrenheit(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Unit of all temperature values and thresholds, Celsius or Fahrenheit"
	::= { cpqCmcSetupGeneral 2 }


cpqCmcsetAudibleAlarm OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enableSilence(2),
	disableSilence(3),
	off(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Audible alarm in CMC unit:
(2): silencing with button on CMC is enabled
(3): silencing with button on CMC is disabled
(4): audible alarm is off (general).
On/off of audible alarm for each event is possible in cpqCmcsetupEvents-group"
	::= { cpqCmcSetupGeneral 3 }


cpqCmcPassword OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..6))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Password to get access to terminal or LCD"
	::= { cpqCmcSetupGeneral 4 }


cpqCmcPasswordOption OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Enable or disable password entry to get access to terminal or LCD"
	::= { cpqCmcSetupGeneral 5 }


cpqCmcquitRelay1 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Enable or disable acknowledging currently active alarm relay 1
(with 'ENTER' on CMC)."
	::= { cpqCmcSetupGeneral 6 }


cpqCmcquitRelay2 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Enable or disable acknowledging currently active alarm relay 2
(with 'ENTER' on CMC)."
	::= { cpqCmcSetupGeneral 7 }


cpqCmclogicRelay1 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	closeAtAlarm(2),
	openAtAlarm(3),
	closeAtEPO(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Logic of Relay 1: (2) Relay will pick up in case of an alarm
(3) Relay will release in case of an alarm
(4) not used"
	::= { cpqCmcSetupGeneral 8 }


cpqCmclogicRelay2 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	closeAtAlarm(2),
	openAtAlarm(3),
	closeAtEPO(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Logic of Relay 2: (2) Relay will pick up in case of an alarm
(3) Relay will release in case of an alarm
(4) not used"
	::= { cpqCmcSetupGeneral 9 }


cpqCmcSetupTemp1Avail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Temperature sensor:
(2) sensor available
(3) sensor not available"
	::= { cpqCmcSetupTemp1 1 }


cpqCmcSetupTemp1RelaysWarn OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of warning condition
of temperature sensor 1:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupTemp1 2 }


cpqCmcSetupTemp1RelaysMax OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of max. alarm condition
of temperature sensor 1:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupTemp1 3 }


cpqCmcSetupTemp1RelaysMin OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of min. alarm condition
of temperature sensor 1:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupTemp1 4 }


cpqCmcSetupTemp1AudibleAlarmWarn OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of warning condition
of temperature sensor 1:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupTemp1 5 }


cpqCmcSetupTemp1AudibleAlarmMax OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of max. alarm condition
of temperature sensor 1:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupTemp1 6 }


cpqCmcSetupTemp1AudibleAlarmMin OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of min. alarm condition
of temperature sensor 1:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupTemp1 7 }


cpqCmcSetupTemp2Avail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Temperature sensor:
(2) sensor available
(3) sensor not available"
	::= { cpqCmcSetupTemp2 1 }


cpqCmcSetupTemp2RelaysWarn OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of warning condition
of temperature sensor 2:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupTemp2 2 }


cpqCmcSetupTemp2RelaysMax OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of max. alarm condition
of temperature sensor 2:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupTemp2 3 }


cpqCmcSetupTemp2RelaysMin OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of min. alarm condition
of temperature sensor 2:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupTemp2 4 }


cpqCmcSetupTemp2AudibleAlarmWarn OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of warning condition
of temperature sensor 2:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupTemp2 5 }


cpqCmcSetupTemp2AudibleAlarmMax OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of max. alarm condition
of temperature sensor 2:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupTemp2 6 }


cpqCmcSetupTemp2AudibleAlarmMin OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of min. alarm condition
of temperature sensor 2:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupTemp2 7 }


cpqCmcSetupFan1Avail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Fan 1:
(2) Fan 1 available
(3) Fan 1 not available"
	::= { cpqCmcSetupFan1 1 }


cpqCmcSetupFan1Relays OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of alarm condition
of Fan 1:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupFan1 2 }


cpqCmcSetupFan1AudibleAlarm OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of alarm condition
of Fan 1:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupFan1 3 }


cpqCmcSetupFan2Avail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Fan 2:
(2) Fan 2 available
(3) Fan 2 not available"
	::= { cpqCmcSetupFan2 1 }


cpqCmcSetupFan2Relays OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of alarm condition
of Fan 2:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupFan2 2 }


cpqCmcSetupFan2AudibleAlarm OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of alarm condition
of Fan 2:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupFan2 3 }


cpqCmcSetupVoltageAvail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Voltage monitoring:
(2) available
(3) not available"
	::= { cpqCmcSetupVoltage 1 }


cpqCmcSetupVoltageRelaysMax OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of max. alarm condition
of voltage monitoring:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupVoltage 2 }


cpqCmcSetupVoltageRelaysMin OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of min. alarm condition
of voltage monitoring:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupVoltage 3 }


cpqCmcSetupVoltageAudibleAlarmMax OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of max. alarm condition
of voltage monitoring:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupVoltage 4 }


cpqCmcSetupVoltageAudibleAlarmMin OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of min. alarm condition
of voltage monitoring:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupVoltage 5 }


cpqCmcSetupHumidityAvail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Humidity sensor:
(2) available
(3) not available"
	::= { cpqCmcSetupHumidity 1 }


cpqCmcSetupHumidityRelaysMax OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of max. alarm condition
of humidity monitoring:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupHumidity 2 }


cpqCmcSetupHumidityRelaysMin OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of min. alarm condition
of humidity monitoring:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupHumidity 3 }


cpqCmcSetupHumidityAudibleAlarmMax OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of max. alarm condition
of humidity monitoring:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupHumidity 4 }


cpqCmcSetupHumidityAudibleAlarmMin OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of min. alarm condition
of humidity monitoring:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupHumidity 5 }


cpqCmcSetupInput1Avail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Input 1 sensor:
(2) available
(3) not available"
	::= { cpqCmcSetupInput1 1 }


cpqCmcSetupInput1Relays OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of a warning condition
of Input 1 (Door/Sidewall open):
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupInput1 2 }


cpqCmcSetupInput1AudibleAlarm OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of a warning condition
of Input 1 (Door/Sidewall open):
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupInput1 3 }


cpqCmcSetupInput1FansOff OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	both(2),
	fan1(3),
	fan2(4),
	noFan(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Fan switching off if Door/Sidewall 1 is opened:
(2) both fans would be switched off
(3) only fan1 will be switched off
(4) only fan2 will be switched off
(5) no fan will be switched off"
	::= { cpqCmcSetupInput1 4 }


cpqCmcSetupInput1ShockSensor OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	on(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Shock sensor function if Door/Sidewall 1 is opened:
(2) Shock Sensor is off (disabled)
(3) Shock Sensor is on (enabled)"
	::= { cpqCmcSetupInput1 5 }


cpqCmcSetupInput1Description OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..18))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Descriptional text of Input1"
	::= { cpqCmcSetupInput1 6 }


cpqCmcSetupInput1Lock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	none(2),
	lock1(3),
	lock2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Door/Sidewall 1 is locked by:
(2) no locking device
(3) locking device 1
(4) locking device 2
(5) both locking devices"
	::= { cpqCmcSetupInput1 7 }


cpqCmcSetupInput2Avail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Input 2 sensor:
(2) available
(3) not available"
	::= { cpqCmcSetupInput2 1 }


cpqCmcSetupInput2Relays OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of a warning condition
of Input 2 (Door/Sidewall open):
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupInput2 2 }


cpqCmcSetupInput2AudibleAlarm OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of a warning condition
of Input 2 (Door/Sidewall open):
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupInput2 3 }


cpqCmcSetupInput2FansOff OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	both(2),
	fan1(3),
	fan2(4),
	noFan(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Fan switching off if Door/Sidewall 2 is opened:
(2) both fans would be switched off
(3) only fan1 will be switched off
(4) only fan2 will be switched off
(5) no fan will be switched off"
	::= { cpqCmcSetupInput2 4 }


cpqCmcSetupInput2ShockSensor OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	on(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Shock sensor function if Door/Sidewall 2 is opened:
(2) Shock Sensor is off (disabled)
(3) Shock Sensor is on (enabled)"
	::= { cpqCmcSetupInput2 5 }


cpqCmcSetupInput2Description OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..18))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Descriptional text of Input2"
	::= { cpqCmcSetupInput2 6 }


cpqCmcSetupInput2Lock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	none(2),
	lock1(3),
	lock2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Door/Sidewall 2 is locked by:
(2) no locking device
(3) locking device 1
(4) locking device 2
(5) both locking devices"
	::= { cpqCmcSetupInput2 7 }


cpqCmcSetupInput3Avail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Input 3 sensor:
(2) available
(3) not available"
	::= { cpqCmcSetupInput3 1 }


cpqCmcSetupInput3Relays OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of a warning condition
of Input 3 (Door/Sidewall open):
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupInput3 2 }


cpqCmcSetupInput3AudibleAlarm OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of a warning condition
of Input 3 (Door/Sidewall open):
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupInput3 3 }


cpqCmcSetupInput3FansOff OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	both(2),
	fan1(3),
	fan2(4),
	noFan(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Fan switching off if Door/Sidewall 3 is opened:
(2) both fans would be switched off
(3) only fan1 will be switched off
(4) only fan2 will be switched off
(5) no fan will be switched off"
	::= { cpqCmcSetupInput3 4 }


cpqCmcSetupInput3ShockSensor OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	on(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Shock sensor function if Door/Sidewall 3 is opened:
(2) Shock Sensor is off (disabled)
(3) Shock Sensor is on (enabled)"
	::= { cpqCmcSetupInput3 5 }


cpqCmcSetupInput3Description OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..18))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Descriptional text of Input3"
	::= { cpqCmcSetupInput3 6 }


cpqCmcSetupInput3Lock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	none(2),
	lock1(3),
	lock2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Door/Sidewall 3 is locked by:
(2) no locking device
(3) locking device 1
(4) locking device 2
(5) both locking devices"
	::= { cpqCmcSetupInput3 7 }


cpqCmcSetupInput4Avail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Input 4 sensor:
(2) available
(3) not available"
	::= { cpqCmcSetupInput4 1 }


cpqCmcSetupInput4Relays OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of a warning condition
of Input 4 (Door/Sidewall open):
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupInput4 2 }


cpqCmcSetupInput4AudibleAlarm OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of a warning condition
of Input 4 (Door/Sidewall open):
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupInput4 3 }


cpqCmcSetupInput4FansOff OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	both(2),
	fan1(3),
	fan2(4),
	noFan(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Fan switching off if Door/Sidewall 4 is opened:
(2) both fans would be switched off
(3) only fan1 will be switched off
(4) only fan2 will be switched off
(5) no fan will be switched off"
	::= { cpqCmcSetupInput4 4 }


cpqCmcSetupInput4ShockSensor OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	on(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Shock sensor function if Door/Sidewall 4 is opened:
(2) Shock Sensor is off (disabled)
(3) Shock Sensor is on (enabled)"
	::= { cpqCmcSetupInput4 5 }


cpqCmcSetupInput4Description OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..18))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Descriptional text of Input4"
	::= { cpqCmcSetupInput4 6 }


cpqCmcSetupInput4Lock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	none(2),
	lock1(3),
	lock2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Door/Sidewall 4 is locked by:
(2) no locking device
(3) locking device 1
(4) locking device 2
(5) both locking devices"
	::= { cpqCmcSetupInput4 7 }


cpqCmcSetupLock1Avail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Door locking device 1:
(2) device available
(3) device not available, no alarm, if door is not locked"
	::= { cpqCmcSetupLock1 1 }


cpqCmcSetupLock1Relays OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of an alarm condition
of Lock 1 (door not locked..):
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupLock1 2 }


cpqCmcSetupLock1RelaysDevice OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of an alarm condition
of Locking device 1 (power fail, low battery...):
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupLock1 3 }


cpqCmcSetupLock1AudibleAlarm OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of an alarm condition
of Lock 1:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupLock1 4 }


cpqCmcSetupLock1AudibleAlarmDevice OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of an alarm condition
of Locking device 1 (power fail, low battery..):
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupLock1 5 }


cpqCmcSetupLock1Time OBJECT-TYPE
	SYNTAX INTEGER (3..600)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Time in seconds while the lock 1 is unlocked
after getting an unlock-command"
	::= { cpqCmcSetupLock1 6 }


cpqCmcSetupLock1PwrFailUnlock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	disabled(2),
	auto(3),
	manual(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Unlock door in case of power fail of locking device:
(2) disabled
(3) auto unlock the door
(4) unlock door with remote signal"
	::= { cpqCmcSetupLock1 7 }


cpqCmcSetupLock1BattLowUnlock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	disabled(2),
	auto(3),
	manual(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Unlock door in case of low battery of locking device:
(2) disabled
(3) auto unlock the door
(4) unlock door with remote signal"
	::= { cpqCmcSetupLock1 8 }


cpqCmcSetupLock1NetFailUnlock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	disabled(2),
	auto(3),
	manual(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Unlock door in case of network failure:
(2) disabled
(3) auto unlock the door
(4) unlock door with remote signal"
	::= { cpqCmcSetupLock1 9 }


cpqCmcSetupLock1LifeFailUnlock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	disabled(2),
	auto(3),
	manual(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Unlock door in case of lifecheck failure (connection CMC<->locking device):
(2) disabled
(3) auto unlock the door
(4) unlock door with remote signal"
	::= { cpqCmcSetupLock1 10 }


cpqCmcSetupLock2Avail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Door locking device 2:
(2) device available
(3) device not available, no alarm, if door is not locked"
	::= { cpqCmcSetupLock2 1 }


cpqCmcSetupLock2Relays OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of an alarm condition
of Lock 2 (door not locked..):
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupLock2 2 }


cpqCmcSetupLock2RelaysDevice OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of an alarm condition
of Locking device 2 (power fail, low battery...):
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupLock2 3 }


cpqCmcSetupLock2AudibleAlarm OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of an alarm condition
of Lock 2:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupLock2 4 }


cpqCmcSetupLock2AudibleAlarmDevice OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of an alarm condition
of Locking device 2 (power fail, low battery..):
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupLock2 5 }


cpqCmcSetupLock2Time OBJECT-TYPE
	SYNTAX INTEGER (3..600)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Time in seconds while the lock 2 is unlocked
after getting an unlock-command"
	::= { cpqCmcSetupLock2 6 }


cpqCmcSetupLock2PwrFailUnlock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	disabled(2),
	auto(3),
	manual(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Unlock door in case of power fail of locking device:
(2) disabled
(3) auto unlock the door
(4) unlock door with remote signal"
	::= { cpqCmcSetupLock2 7 }


cpqCmcSetupLock2BattLowUnlock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	disabled(2),
	auto(3),
	manual(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Unlock door in case of low battery of locking device:
(2) disabled
(3) auto unlock the door
(4) unlock door with remote signal"
	::= { cpqCmcSetupLock2 8 }


cpqCmcSetupLock2NetFailUnlock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	disabled(2),
	auto(3),
	manual(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Unlock door in case of network failure:
(2) disabled
(3) auto unlock the door
(4) unlock door with remote signal"
	::= { cpqCmcSetupLock2 9 }


cpqCmcSetupLock2LifeFailUnlock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	disabled(2),
	auto(3),
	manual(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Unlock door in case of lifecheck failure (connection CMC<->locking device):
(2) disabled
(3) auto unlock the door
(4) unlock door with remote signal"
	::= { cpqCmcSetupLock2 10 }


cpqCmcSetupSmokeAvail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Smoke sensor:
(2) available
(3) not available"
	::= { cpqCmcSetupSmoke 1 }


cpqCmcSetupSmokeRelays OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of an alarm condition
of Smoke Sensor:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupSmoke 2 }


cpqCmcSetupSmokeAudibleAlarm OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of an alarm condition
of Smoke Sensor:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupSmoke 3 }


cpqCmcSetupSmokeFansOff OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	both(2),
	fan1(3),
	fan2(4),
	noFan(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Fan switching off if in case of smoke-alarm:
(2) both fans would be switched off
(3) only fan1 will be switched off
(4) only fan2 will be switched off
(5) no fan will be switched off"
	::= { cpqCmcSetupSmoke 4 }


cpqCmcSetupSmokeUnlock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	both(2),
	lock1(3),
	lock2(4),
	noLock(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Lock is unlocked in case of smoke-alarm:
(2) both locks will be unlocked
(3) only lock1 will be unlocked
(4) only lock2 will be unlocked
(5) no lock will be unlocked"
	::= { cpqCmcSetupSmoke 5 }


cpqCmcSetupShockAvail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Shock sensor:
(2) available
(3) not available"
	::= { cpqCmcSetupShock 1 }


cpqCmcSetupShockRelays OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of an alarm condition
of Shock Sensor:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupShock 2 }


cpqCmcSetupShockAudibleAlarm OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of an alarm condition
of Shock Sensor:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupShock 3 }


cpqCmcSetupShockSensitivity OBJECT-TYPE
	SYNTAX INTEGER (1..10)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Sensitivity of shock-sensor.
1 = low sensitivity, 10 = high sensitivity"
	::= { cpqCmcSetupShock 4 }


cpqCmcSetupAux1Avail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Aux 1 sensor:
(2) available
(3) not available"
	::= { cpqCmcSetupAux1 1 }


cpqCmcSetupAux1Relays OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of an alarm condition
of Aux 1:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupAux1 2 }


cpqCmcSetupAux1AudibleAlarm OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of an alarm condition
of Aux 1:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupAux1 3 }


cpqCmcSetupAux1InputType OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	normOpen(2),
	normClosed(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Type of other digital input (used for any digital signal):
(2) contact is normally open, no alarm if contact is open,
alarm if contact is closed
(3) contact is normally closed, no alarm if contact is closed,
alarm if contact is open"
	::= { cpqCmcSetupAux1 4 }


cpqCmcSetupAux1Description OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..18))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Descriptional text of the digital input (Aux1) "
	::= { cpqCmcSetupAux1 5 }


cpqCmcSetupAux1Unlock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	noLock(2),
	lock1(3),
	lock2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Lock will be unlocked with Aux-Input 1:
(2) no lock will be unlocked
(3) only lock1 will be unlocked
(4) only lock2 will be unlocked
(5) both locks will be unlocked"
	::= { cpqCmcSetupAux1 6 }


cpqCmcSetupAux2Avail OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	available(2),
	notAvailable(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Aux 2 sensor:
(2) available
(3) not available"
	::= { cpqCmcSetupAux2 1 }


cpqCmcSetupAux2Relays OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of an alarm condition
of Aux 2:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupAux2 2 }


cpqCmcSetupAux2AudibleAlarm OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of an alarm condition
of Aux 2:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupAux2 3 }


cpqCmcSetupAux2InputType OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	normOpen(2),
	normClosed(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Type of other digital input (used for any digital signal):
(2) contact is normally open, no alarm if contact is open,
alarm if contact is closed
(3) contact is normally closed, no alarm if contact is closed,
alarm if contact is open"
	::= { cpqCmcSetupAux2 4 }


cpqCmcSetupAux2Description OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..18))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Descriptional text of the digital input (Aux2) "
	::= { cpqCmcSetupAux2 5 }


cpqCmcSetupAux2Unlock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	noLock(2),
	lock1(3),
	lock2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Lock will be unlocked with Aux-Input 2:
(2) no lock will be unlocked
(3) only lock1 will be unlocked
(4) only lock2 will be unlocked
(5) both locks will be unlocked"
	::= { cpqCmcSetupAux2 6 }


cpqCmcSetupAlarm1Relays OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of an alarm condition
of Alarm 1:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupAlarm1 1 }


cpqCmcSetupAlarm1AudibleAlarm OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of an alarm condition
of Alarm 1:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupAlarm1 2 }


cpqCmcSetupAlarm1Description OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..18))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Descriptional text of alarm 1"
	::= { cpqCmcSetupAlarm1 3 }


cpqCmcSetupAlarm2Relays OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	off(2),
	relay1(3),
	relay2(4),
	both(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Alarm Relays in case of an alarm condition
of Alarm 2:
(2) no switching of Relays
(3) Relay 1 will switch
(4) Relay 2 will switch
(5) both Relays will switch"
	::= { cpqCmcSetupAlarm2 1 }


cpqCmcSetupAlarm2AudibleAlarm OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Alert handling of Audible Alarm of in case of an alarm condition
of Alarm 2:
(2) Start Audible Alarm
(3) No Audible Alarm"
	::= { cpqCmcSetupAlarm2 2 }


cpqCmcSetupAlarm2Description OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..18))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Descriptional text of alarm 2"
	::= { cpqCmcSetupAlarm2 3 }


cpqCmcSetupDate OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..10))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "actual Date in format DD.MM.YYYY"
	::= { cpqCmcSetupClock 1 }


cpqCmcSetupTime OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..8))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "actual Time in format HH:MM:SS, HH (0-23), MM (0-59), SS (0-59)"
	::= { cpqCmcSetupClock 2 }


cpqCmcThresholdMaxTemp1 OBJECT-TYPE
	SYNTAX INTEGER (0..200)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Threshold value maximum temperature 1"
	::= { cpqCmcSetupThreshold 1 }


cpqCmcThresholdWarningTemp1 OBJECT-TYPE
	SYNTAX INTEGER (0..200)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Threshold value warning temperature 1"
	::= { cpqCmcSetupThreshold 2 }


cpqCmcThresholdMinTemp1 OBJECT-TYPE
	SYNTAX INTEGER (0..100)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Threshold value minimum temperature 1"
	::= { cpqCmcSetupThreshold 3 }


cpqCmcThresholdMaxTemp2 OBJECT-TYPE
	SYNTAX INTEGER (0..200)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Threshold value maximum temperature 2"
	::= { cpqCmcSetupThreshold 4 }


cpqCmcThresholdWarningTemp2 OBJECT-TYPE
	SYNTAX INTEGER (0..200)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Threshold value warning temperature 2"
	::= { cpqCmcSetupThreshold 5 }


cpqCmcThresholdMinTemp2 OBJECT-TYPE
	SYNTAX INTEGER (0..100)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Threshold value minimum temperature 2"
	::= { cpqCmcSetupThreshold 6 }


cpqCmcThresholdFan1 OBJECT-TYPE
	SYNTAX INTEGER (0..200)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Threshold Fan 1 in deg F or deg C, Fan 1 will start
if temperature 1 exceeds this value"
	::= { cpqCmcSetupThreshold 7 }


cpqCmcThresholdFan1Hysteresis OBJECT-TYPE
	SYNTAX INTEGER (1..20)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Hystersis of Fan 1, Fan 1 will stop if temperature 1 falls below
value of cpqCmcThresholdFan1 minus cpqCmcThresholdFan1Hysteresis"
	::= { cpqCmcSetupThreshold 8 }


cpqCmcThresholdFan2 OBJECT-TYPE
	SYNTAX INTEGER (0..200)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Threshold Fan 2 in deg F or deg C, Fan 2 will start
if temperature 2 exceeds this value"
	::= { cpqCmcSetupThreshold 9 }


cpqCmcThresholdFan2Hysteresis OBJECT-TYPE
	SYNTAX INTEGER (1..20)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Hystersis of Fan 2, Fan 2 will stop if temperature 2 falls below
value of cpqCmcThresholdFan2 minus cpqCmcThresholdFan2Hysteresis"
	::= { cpqCmcSetupThreshold 10 }


cpqCmcThresholdMaxVoltage OBJECT-TYPE
	SYNTAX INTEGER (0..255)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Threshold high value Voltage alarm"
	::= { cpqCmcSetupThreshold 11 }


cpqCmcThresholdMinVoltage OBJECT-TYPE
	SYNTAX INTEGER (0..255)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Threshold low value Voltage alarm"
	::= { cpqCmcSetupThreshold 12 }


cpqCmcThresholdMaxHumidity OBJECT-TYPE
	SYNTAX INTEGER (0..100)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Threshold high value Humidity alarm"
	::= { cpqCmcSetupThreshold 13 }


cpqCmcThresholdMinHumidity OBJECT-TYPE
	SYNTAX INTEGER (0..100)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Threshold low value Humidity alarm"
	::= { cpqCmcSetupThreshold 14 }


cpqCmcTrapTableNumber OBJECT-TYPE
	SYNTAX INTEGER
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Number of trapTable entries. The number of trap-receivers"
	::= { cpqCmcTraps 1 }


cpqCmcTrapTable OBJECT-TYPE
	SYNTAX SEQUENCE OF CpqCmcTrapEntry
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "A list of trap-receiver entries"
	::= { cpqCmcTraps 2 }


cpqCmcTrapEntry OBJECT-TYPE
	SYNTAX CpqCmcTrapEntry
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Entries of trapTable"
	INDEX { cpqCmcTrapIndex  }

	::= { cpqCmcTrapTable 1 }

cpqCmcTrapEntry ::=
	SEQUENCE {
		cpqCmcTrapIndex INTEGER,
		cpqCmcTrapStatus INTEGER,
		cpqCmcTrapIPaddress DisplayString
		}

cpqCmcTrapIndex OBJECT-TYPE
	SYNTAX INTEGER (1..4)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Index for the trap-receiver-table. Its value ranges between
1 and the value of cpqCmcTrapTableNumber "
	::= { cpqCmcTrapEntry 1 }


cpqCmcTrapStatus OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	enabled(2),
	disabled(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Enable or disable trap receiver"
	::= { cpqCmcTrapEntry 2 }


cpqCmcTrapIPaddress OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..15))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "IP-address of trap-receiver"
	::= { cpqCmcTrapEntry 3 }


cpqCmcValueTemp1 OBJECT-TYPE
	SYNTAX INTEGER
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Actual temperature value of temperature sensor 1 in deg C or deg F"
	::= { cpqCmcValues 1 }


cpqCmcValueTemp2 OBJECT-TYPE
	SYNTAX INTEGER
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Actual temperature value of temperature sensor 2 in deg C or deg F"
	::= { cpqCmcValues 2 }


cpqCmcValueVoltage OBJECT-TYPE
	SYNTAX INTEGER
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Actual value of power supply (voltage monitoring and fans) in V"
	::= { cpqCmcValues 3 }


cpqCmcValueHumidity OBJECT-TYPE
	SYNTAX INTEGER
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Actual value of humidity
0..100%"
	::= { cpqCmcValues 4 }


cpqCmcValueOperatingTime OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..31))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Operating time CMC-unit"
	::= { cpqCmcValues 5 }


cpqCmcStatusTemp1 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	normal(2),
	warning(3),
	overMax(4),
	underMin(5),
	noSensor(6),
	error(7)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The status of temperature 1,
see thresholds of temperature 1:
(2) temperature normal
(3) temperature exceeds warning threshold
(4) temperature exceeds max. threshold
(5) temperature drops under min. threshold
(6) no sensor connected, not available
(7) error, sensor disconnected"
	::= { cpqCmcStatus 1 }


cpqCmcStatusTemp2 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	normal(2),
	warning(3),
	overMax(4),
	underMin(5),
	noSensor(6),
	error(7)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The status of temperature 2,
see thresholds of temperature 2:
(2) temperature normal
(3) temperature exceeds warning threshold
(4) temperature exceeds max. threshold
(5) temperature drops under min. threshold
(6) no sensor connected, not available
(7) error, sensor disconnected"
	::= { cpqCmcStatus 2 }


cpqCmcStatusFan1 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	autoOff(2),
	autoOn(3),
	manualOff(4),
	manualOn(5),
	smokeOff(6),
	doorOff(7),
	noFan(8),
	error(9)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The status of fan 1:
(2) fan is switched off by temperature sensor 1
(3) fan is switched on by temperature sensor 1
(4) fan is switched off by Manual Control (cpqCmcSetFan1)
(5) fan is switched on by Manual Control (cpqCmcSetFan1)
(6) fan is switched off because of smoke alarm
(7) fan is switched off because door is open
(8) no fan
(9) fan error, current monitoring"
	::= { cpqCmcStatus 3 }


cpqCmcStatusFan2 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	autoOff(2),
	autoOn(3),
	manualOff(4),
	manualOn(5),
	smokeOff(6),
	doorOff(7),
	noFan(8),
	error(9)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The status of fan 2:
(2) fan is switched off by temperature sensor 2
(3) fan is switched on by temperature sensor 2
(4) fan is switched off by Manual Control (cpqCmcSetFan2)
(5) fan is switched on by Manual Control (cpqCmcSetFan2)
(6) fan is switched off because of smoke alarm
(7) fan is switched off because door is open
(8) no fan
(9) fan error, current monitoring"
	::= { cpqCmcStatus 4 }


cpqCmcStatusVoltage OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	normal(2),
	overMax(3),
	underMin(4),
	noVoltage(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The voltage-status,
see thresholds of power supply:
(2) voltage normal
(3) voltage exceeds max. threshold
(4) voltage drops under min. threshold
(5) no power connected"
	::= { cpqCmcStatus 5 }


cpqCmcStatusHumidity OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	normal(2),
	overMax(3),
	underMin(4),
	noSensor(5),
	error(6)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The humidity-status,
see thresholds of humidity:
(2) humidity normal
(3) humidity exceeds max. threshold
(4) humidity drops under min. threshold
(5) no sensor connected, not available
(6) error, sensor disconnected"
	::= { cpqCmcStatus 6 }


cpqCmcStatusInput1 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	closed(2),
	open(3),
	noSensor(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The status of door/sidepanel 1, closed (2), open (3)
or no sensor connected (4)"
	::= { cpqCmcStatus 7 }


cpqCmcStatusInput2 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	closed(2),
	open(3),
	noSensor(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The status of door/sidepanel 2, closed (2), open (3)
or no sensor connected (4)"
	::= { cpqCmcStatus 8 }


cpqCmcStatusInput3 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	closed(2),
	open(3),
	noSensor(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The status of door/sidepanel 3, closed (2), open (3)
or no sensor connected (4)"
	::= { cpqCmcStatus 9 }


cpqCmcStatusInput4 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	closed(2),
	open(3),
	noSensor(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The status of door/sidepanel 4, closed (2), open (3)
or no sensor connected (4)"
	::= { cpqCmcStatus 10 }


cpqCmcStatusLock1Lock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	locked(2),
	unlockedAuto(3),
	unlockedTime(4),
	unlockedSmoke(5),
	unlockedKey(6),
	unlockedPwrFail(7),
	unlockedBattLow(8),
	unlockedNetFail(9),
	unlockedConnFail(10),
	readyToLock(11),
	alarm(12),
	configError(13),
	notAvail(14)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The status of door locking 1
(2) Door locking-device is activated, door is locked
(3) Door locking-device is not activated, door is unlocked by Network Management
(4) Door locking-device is not activated for x sec, time see
cpqCmcSetupLock1Time, door is unlocked by Network Management
(5) Door locking-device is not activated, door is unlocked because of Smoke alarm
(6) Door is unlocked from remote-signal
(7) Door locking-device is not activated, door is unlocked
because of Power Fail of locking device
(8) Door locking-device is not activated, door is unlocked
because of low Battery of locking device
(9) Door locking-device is not activated, door is unlocked
because of Network Fail
(10)Door locking-device is not activated, door is unlocked
because of connection fail, no connection locking device <-> CMC
(11)Door locking-device is ready to lock, lock will be activated after doors are closed
(12)Door locking-device is activated but door is not locked, alarm
(13)Configuration error, association door to locking-device missing
(14)Lock not installed"
	::= { cpqCmcStatus 11 }


cpqCmcStatusLock2Lock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	locked(2),
	unlockedAuto(3),
	unlockedTime(4),
	unlockedSmoke(5),
	unlockedKey(6),
	unlockedPwrFail(7),
	unlockedBattLow(8),
	unlockedNetFail(9),
	unlockedConnFail(10),
	readyToLock(11),
	alarm(12),
	configError(13),
	notAvail(14)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The status of door locking 2
(2) Door locking-device is activated, door is locked
(3) Door locking-device is not activated, door is unlocked by Network Management
(4) Door locking-device is not activated for x sec, time see
cpqCmcSetupLock1Time, door is unlocked by Network Management
(5) Door locking-device is not activated, door is unlocked because of Smoke alarm
(6) Door is unlocked from remote-signal
(7) Door locking-device is not activated, door is unlocked
because of Power Fail of locking device
(8) Door locking-device is not activated, door is unlocked
because of low Battery of locking device
(9) Door locking-device is not activated, door is unlocked
because of Network Fail
(10)Door locking-device is not activated, door is unlocked
because of connection fail, no connection locking device <-> CMC
(11)Door locking-device is ready to lock, lock will be activated after doors are closed
(12)Door locking-device is activated but door is not locked, alarm
(13)Configuration error, association door to locking-device missing
(14)Lock not installed"
	::= { cpqCmcStatus 12 }


cpqCmcStatusSmoke OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	cleared(2),
	present(3),
	noSensor(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Status smoke-sensor, OK (2), smoke detected (3)
or no sensor connected (4)"
	::= { cpqCmcStatus 13 }


cpqCmcStatusShock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	cleared(2),
	present(3),
	noSensor(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Status Shock sensor, OK (2), shock detected (3)
or no sensor connected (4)"
	::= { cpqCmcStatus 14 }


cpqCmcStatusAux1 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	ok(2),
	alarm(3),
	noSensor(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Status aux. digital input"
	::= { cpqCmcStatus 15 }


cpqCmcStatusAux2 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	ok(2),
	alarm(3),
	noSensor(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Status aux. digital input"
	::= { cpqCmcStatus 16 }


cpqCmcStatusAlarm1 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	ok(2),
	alarm(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Status of alarm 1, see cmpCmcsetAlarm1. This alarm can be set from
the Network management system. A descriptional text for this alarm
can be set in cpqCmcSetupAlarm1Description."
	::= { cpqCmcStatus 17 }


cpqCmcStatusAlarm2 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	ok(2),
	alarm(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Status of alarm 2, see cmpCmcsetAlarm2. This alarm can be set from
the Network management system. A descriptional text for this alarm
can be set in cpqCmcSetupAlarm2Description."
	::= { cpqCmcStatus 18 }


cpqCmcStatusLock1Dev OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	ok(2),
	powerFail(3),
	lowBattery(4),
	replaceBatt(5),
	missingBatt(6),
	noConnect(7),
	notAvail(8)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The status of door-locking device 1
(2) OK
(3) Power fail of door locking-device
(4) Low Battery of door locking-device
(5) Battery of door locking device needs to be replaced
(6) Battery missing, insert all batteries
(7) Connection CMC->door locking device lost
(8) Lock not installed"
	::= { cpqCmcStatus 19 }


cpqCmcStatusLock2Dev OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	ok(2),
	powerFail(3),
	lowBattery(4),
	replaceBatt(5),
	missingBatt(6),
	noConnect(7),
	notAvail(8)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "The status of door-locking device 2
(2) OK
(3) Power fail of door locking-device
(4) Low Battery of door locking-device
(5) Battery of door locking device needs to be replaced
(6) Battery missing, insert all batteries
(6) Connection CMC->door locking device lost
(7) Lock not installed"
	::= { cpqCmcStatus 20 }


cpqCmcStatusAccess OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..31))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Status access, for future use"
	::= { cpqCmcControl 1 }


cpqCmcSetLock1Lock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	lockDoor(2),
	openDoorTime(3),
	openDoor(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Set door locking device 1, see table
With this command the management-station can set the conditions for
the door locking device
(2) Door will be locked
(3) Door will be unlocked for a defined time,
time can be changed, see cpqCmcSetupLock1Time
(4) Door is generally unlocked
Locking and unlocking with this command can not be
enabled or disabled with cpqCmcSetLock1Key-command"
	::= { cpqCmcControl 2 }


cpqCmcSetLock1Key OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	disable(2),
	enableBoth(3),
	enableKeypad(4),
	enableRemoteInput(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Enable or disable unlocking of the rack-door with external components
like keypad or remote input.
With this command the management station can set the conditions for
unlocking the door:
(2) unlocking is disabled, no unlocking with keypad or remote input
(3) unlocking with keypad or remote signal (both) is enabled
(4) unlocking with keypad (only) is enabled
(5) unlocking with remote input (only) is enabled
Unlocking door with the cpqCmcSetLock1Lock-command does not depend
on this variable"
	::= { cpqCmcControl 3 }


cpqCmcSetLock2Lock OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	lockDoor(2),
	openDoorTime(3),
	openDoor(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Set door locking device 2, see table
With this command the management-station can set the conditions for
the door locking device
(2) Door will be locked
(3) Door will be unlocked for a defined time,
time can be changed, see cpqCmcSetupLock2Time
(4) Door is generally unlocked
Locking and unlocking with this command can not be
enabled or disabled with cpqCmcSetLock2Key-command"
	::= { cpqCmcControl 4 }


cpqCmcSetLock2Key OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	disable(2),
	enableBoth(3),
	enableKeypad(4),
	enableRemoteInput(5)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Enable or disable unlocking of the rack-door with external components
like keypad or remote input.
With this command the management-station can set the conditions for
unlocking the door:
(2) unlocking is disabled, no unlocking with keypad or remote input
(3) unlocking with keypad or remote signal (both) is enabled
(4) unlocking with keypad (only) is enabled
(5) unlocking with remote input (only) is enabled
Unlocking door with the cpqCmcSetDoor2-command does not depend
on this variable"
	::= { cpqCmcControl 5 }


cpqCmcSetMessage OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..31))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Set message to CMC, for future use"
	::= { cpqCmcControl 6 }


cpqCmcSetAlarm1 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	clearAlarm(2),
	setAlarm(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Is used to set an alarm in the CMC from the management-station.
With this command the management-station can i.e. switch on an
alarm-relay or the AudibleAlarm of the CMC.
Can be used for alert-handling"
	::= { cpqCmcControl 7 }


cpqCmcSetAlarm2 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	clearAlarm(2),
	setAlarm(3)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Is used to set an alarm in the CMC from the management-station.
With this command the management-station can i.e. switch on an
alarm-relay or the AudibleAlarm of the CMC.
Can be used for alert-handling"
	::= { cpqCmcControl 8 }


cpqCmcSetFan1 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	auto(2),
	on(3),
	off(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Is used for run and stop control of fan1.
(2) fan will run and stop according to temperature of sensor 1
and threshold of fan1
(3) fan will run independent of temperature and threshold
(4) fan will stop independent of temperature and threshold
(3) and (4) can be used for alert handling."
	::= { cpqCmcControl 9 }


cpqCmcSetFan2 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	auto(2),
	on(3),
	off(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Is used for run and stop control of fan2.
(2) fan will run and stop according to temperature of sensor 2
and threshold of fan2
(3) fan will run independent of temperature and threshold
(4) fan will stop independent of temperature and threshold
(3) and (4) can be used for alert handling"
	::= { cpqCmcControl 10 }


cpqCmcSetQuitRelay1 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	switched(2),
	notSwitched(3),
	quit(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Status and quit of alarm relay 1.
(2) relay is switched because of an alarm
(3) relay is not switched, no alarm
(4) (set) will quit relay 1 in case of alarm"
	::= { cpqCmcControl 11 }


cpqCmcSetQuitRelay2 OBJECT-TYPE
	SYNTAX INTEGER {
	other(1),
	switched(2),
	notSwitched(3),
	quit(4)
	}
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Status and quit of alarm relay 2.
(2) relay is switched because of an alarm
(3) relay is not switched, no alarm
(4) (set) will quit relay 2 in case of alarm"
	::= { cpqCmcControl 12 }


cpqCmcLogsNumber OBJECT-TYPE
	SYNTAX INTEGER (0..100)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Number of Log-entries"
	::= { cpqCmcLog 1 }


cpqCmcLogTable OBJECT-TYPE
	SYNTAX SEQUENCE OF CpqCmcLogEntry
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Log-table"
	::= { cpqCmcLog 2 }


cpqCmcLogEntry OBJECT-TYPE
	SYNTAX CpqCmcLogEntry
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Log-table entries"
	INDEX { cpqCmcLogIndex  }

	::= { cpqCmcLogTable 1 }

cpqCmcLogEntry ::=
	SEQUENCE {
		cpqCmcLogIndex INTEGER,
		cpqCmcLogDate DisplayString,
		cpqCmcLogTime DisplayString,
		cpqCmcLogText DisplayString,
		cpqCmcLogClass DisplayString
		}

cpqCmcLogIndex OBJECT-TYPE
	SYNTAX INTEGER (1..100)
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Index for the Log-table. Its value ranges between
1 and the value of cpqCmcLogsNumber "
	::= { cpqCmcLogEntry 1 }


cpqCmcLogDate OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..11))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Date of log information. "
	::= { cpqCmcLogEntry 2 }


cpqCmcLogTime OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..11))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Time of log information. "
	::= { cpqCmcLogEntry 3 }


cpqCmcLogText OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..31))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Log information. "
	::= { cpqCmcLogEntry 4 }


cpqCmcLogClass OBJECT-TYPE
	SYNTAX DisplayString (SIZE(0..31))
	ACCESS read-only
	STATUS mandatory
	DESCRIPTION "Status of log information. "
	::= { cpqCmcLogEntry 5 }


cpqCmcalarm2 TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusAlarm2 }
      --#SUMMARY "Location: %s, Message: %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "NMSalarm (153018)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "Alarm 2, set from Network management"
      ::= 153018


cpqCmcalarmTemp1 TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusTemp1 }
      --#SUMMARY "Location: %s, Message: Rack temp sensor 1 %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Temperaturealarm (153001)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The temperature at rack sensor 1 is outside the specified threshold.  Action: Check the air handling system for the rack and refer to Trap Details for more information."
      ::= 153001


cpqCmcalarm1 TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusAlarm1 }
      --#SUMMARY "Location: %s, Message: %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "NMSalarm (153017)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "Alarm 1, set from Network management"
      ::= 153017


cpqCmcalarmLock1Dev TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusLock1Dev }
      --#SUMMARY "Location: %s, Status: door lock device #1 %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Doorlockingalarm of device (153019)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The rack door locking device #1 has failed.  Action: Check the device lock cable or failed battery and refer to Trap Details for more information."
      ::= 153019


cpqCmcalarmFan2 TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusFan2 }
      --#SUMMARY "Location: %s, Rack fan 2 status: %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Fanalarm (153004)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The status of Fan 2 has changed.  Action: Refer to Trap Details for more information."
      ::= 153004


cpqCmcalarmFan1 TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusFan1 }
      --#SUMMARY "Location: %s, Rack fan 1 status: %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Fanalarm (153003)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The status of Fan 1 has changed.  Action: Refer to Trap Details for more information."
      ::= 153003


cpqCmcalarmVoltage TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusVoltage }
      --#SUMMARY "Location: %s, Message: Rack supply voltage %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Voltagealarm (153005)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The AC voltage of the rack is outside the specified threshold.  Action: Check the incoming power source and ensure all cables are inserted correctly."
      ::= 153005


cpqCmcalarmLock2Dev TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusLock2Dev }
      --#SUMMARY "Location: %s, Status: door lock device #2 %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Doorlockingalarm of device (153020)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The rack door locking device #2 has failed.  Action: Check the device lock cable or failed battery and refer to Trap Details for more information."
      ::= 153020


cpqCmcalarmShock TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusShock }
      --#SUMMARY "Location: %s, Message: Rack shock detector  shock: %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Shockalarm (153014)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The rack shock detector has detected a vibration to the rack.  Action: Investigate rack."
      ::= 153014


cpqCmcalarmLock2 TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusLock2Lock }
      --#SUMMARY "Location: %s, Message: Rack lock #1 %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Doorlockingalarm (153012)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "Rack door lock #2 alarm.  Action: Ensure the door is completely closed and check for unauthorized intrusion and refer to Trap Details for more information."
      ::= 153012


cpqCmcalarmLock1 TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusLock1Lock }
      --#SUMMARY "Location: %s, Message: Rack lock #1 %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Doorlockingalarm (153011)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "Rack door lock #1 alarm.  Action: Ensure the door is completely closed and check for unauthorized intrusion and refer to Trap Details for more information."
      ::= 153011


cpqCmcalarmHumidity TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusHumidity }
      --#SUMMARY "Location: %s, Message: %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Humidityalarm (153006)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The humidity of the rack is outside the specified threshold.  Action: Check the air handling system for the rack and refer to Trap Details for more information."
      ::= 153006


cpqCmcSetupChanged TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation }
      --#SUMMARY "Location: %s, Name: %s, contact %s"
      --#ARGUMENTS {3,2,1}
      --#SEVERITY INFORMATIONAL
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: #"
      --#TYPE "Setup has changed (153100)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "Setup of CMC has changed."
      ::= 153100


cpqCmcalarmInput4 TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusInput4 }
      --#SUMMARY "Location: %s, Message: Rack access point 4 %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MINOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Door/sidepanelalarm (153010)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The door or sidepanel of the rack has been opened (access point #4).  Action: Check for unauthorized intrusion and refer to Trap Details for more information."
      ::= 153010


cpqCmcalarmInput3 TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusInput3 }
      --#SUMMARY "Location: %s, Message: Rack access point 3 %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MINOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Door/sidepanelalarm (153009)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The door or sidepanel of the rack has been opened (access point #3).  Action: Check for unauthorized intrusion and refer to Trap Details for more information."
      ::= 153009


cpqCmcalarmInput2 TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusInput2 }
      --#SUMMARY "Location: %s, Message: Rack access point 2 %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MINOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Door/sidepanelalarm (153008)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The door or sidepanel of the rack has been opened (access point #2).  Action: Check for unauthorized intrusion and refer to Trap Details for more information."
      ::= 153008


cpqCmcalarmInput1 TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusInput1 }
      --#SUMMARY "Location: %s, Message: Rack access point 1 %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MINOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Door/sidepanelalarm (153007)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The door or sidepanel of the rack has been opened (access point #1).  Action: Check for unauthorized intrusion and refer to Trap Details for more information."
      ::= 153007


cpqCmcalarmSmoke TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusSmoke }
      --#SUMMARY "Location: %s, Message: Rack smoke detector  smoke: %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Smokealarm (153013)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The rack smoke detector has detected smoke.  Action: Investigate rack for an over temperature condition and refer to Trap Details for more information."
      ::= 153013


cpqCmcalarmAux2 TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusAux2 }
      --#SUMMARY "Location: %s, Message: aux input #2 %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Auxalarm (153016)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The rack auxiliary alarm input #2 has been triggered."
      ::= 153016


cpqCmcalarmAux1 TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusAux1 }
      --#SUMMARY "Location: %s, Message: aux input #1 %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Auxalarm (153015)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The rack auxiliary alarm input #1 has been triggered."
      ::= 153015


cpqCmcalarmTemp2 TRAP-TYPE
      ENTERPRISE cpqCmc
      VARIABLES { sysDescr, sysContact, sysName, sysLocation, cpqCmcStatusTemp2 }
      --#SUMMARY "Location: %s, Message: Rack temp sensor 2 %s from: %s, contact %s"
      --#ARGUMENTS {3,4,2,1}
      --#SEVERITY MAJOR
      --#TIMEINDEX 99
      --#MSG_FORMATTER "$V1V#Description: # $V2V#Contact: # $V4V#Location: # $V5V#Status: #"
      --#TYPE "Temperaturealarm (153002)"
      --#ENABLE true
      --#CATEGORY "Proliant Remote Management Events"
DESCRIPTION "The temperature at rack sensor 2 is outside the specified threshold.  Action: Check the air handling system for the rack and refer to Trap Details for more information."
      ::= 153002


END
